Emerson 3308 echo curve
How can I access the echo curve of the 3308 radar and how is this information relevant to me?.
Expert’s answer: How to access the Emerson 3308 echo curve
Usually, the basic specs of the Emerson 3308 will give you a stable level measurement. However, you can use the Emerson 3308 echo curve as a troubleshooting tool where you get a view of the tank signal. So if you want to access the echo curve from the home screen:
Service Tools > Echo Tuning > Echo Curve
You can also access the echo curve through plant asset management software or a handheld. If you have interference in your level measurement, you’ll need to set up the thresholds. However, the default setup should do in most cases.
The signal amplitude thresholds separate the measurement from disturbing echoes and noise.
Radar level meters on the market:
Other resources that might interest you
How to fix Endress+Hauser FMP51 output signal?
The output for our E+H Levelflex FMP51 isn’t changing proportionally with the level. Why is that?
Rosemount 8712 and another flow sensor
Can I pair a Rosemount 8712 with another brand sensor?
Product Review: Rosemount 8800 Multivariable
Want a review of the Rosemount 8800 Multivariable? Then, check this product review!
Multifunctional switch panel process measuring device for monitoring and displaying analog measured values