Expert’s answer: Radar level transmitter for low dielectric
Yes, you can use a radar level transmitter for low dielectric! But which one? Ah, therein lies the dilemma. To guide your decision, you need to nail down the process details.
For instance, “below 3” gets you started in the right direction, but you need to know your specific dielectric constant value to pick the right device for your process. The FMR 10 from Endress+Hauser requires a minimum dielectric constant (DC) of 4. However, this device falls on the “cost-effective” end of the quality scale.
If you review the VEGAPULS 64, then you’ll find that you can have a value of 1.6 if you have the device installed in a bypass or surge pipe. This means you’ll need to review your setup as well. You also have to check your tank specs. If you have vapor or foam on your product, then those conditions can affect your measurements too.
You see? You have many factors to review besides your dielectric constant. Once you have all these details gathered up, you can review the available devices on the market and see which will suit your process best.
Try these companies on for size:
Other resources that might interest you
Radar level measurement
Could you please explain how radar works to measure level? So you’re wondering how radar level measurement works? We can certainly explain this. Radar level meters work based on the time of flight (TOF) method or time domain reflectometry (TDR).
Pressure – Measurement troubleshooting
We’re a multinational company based in the Caribbean and have purchased DP level transmitters for our tank farms. We installed the same devices in our new plan in northern Europe, but we noticed that the measurements are not correct. Could you please advise us regarding the source of this problem?
Level transmitter malfunction
We have the Endress+Hauser Levelflex FMP51 installed on a diesel tank for level measurement, but its output is not changing proportionally to the tank level. In the control room, we simulated different currents from the transmitter function menu and the transmitter responded fine. What do we need to fix?