Vortex flow meter installation
Ooh, ow, hotcha, vortex flow meter installation! Yeah, if you’ve got high temps, then you definitely need to factor that into your vortex setup. According to Emerson, you have two different ways you can do it with the Rosemount 8600.
As a utility vortex meter, it can measure liquid and steam. Totally irrelevant, but for those of you who’ve never seen one, check it out. The guys obviously modeled it after a Tyrannosaurus Rex, but they forgot the tiny arms!
Anyway, when you have high temps, you need to set up the 8600 in one of the positions below:
Yeah, they recommend installing it head up for the best results, but the material covering your pipe will interfere. Don’t worry, one of these setups will still give you good results.
Now hold on, don’t run off yet! You also need to make sure you have straight pipe before and after the flow meter. Okay, now you can go! Get that vortex online!
More flow meters:
You can read more about Vortex flow meters:
Vortex flow meters in low flow profile – I never knew the impact vortex flow meters could have until I saw my signal trends disappear in low flow mode. So what applications suit vortex meters best? Read more
Orifice plate or vortex for steam flow meter? – I need a new flow meter for steam measurement. I know we can use a vortex flow meter or an orifice plate. Which do you recommend? Read more
Vortex limitations – I need to measure my air flow and heard that a vortex is a good solution. I also heard that it has limitations though! Can you tell me more? Read more