I have a level transmitter with capillary, and I need to do the level calculation. The transmitter is one meter below the takeoff point, and the tank's takeoff point is five meters. The product's specific gravity is 0.89, and the capillary is filled with glycol at a specific gravity of 1.02. How can I calculate the level range?
Expert’s answer: Level calculation for pressure transmitter with capillary
So, you need to learn how to do level calculation for pressure transmitter with capillary? Okay, here’s what you need to know:
Level calculation never changes on a differential pressure transmitter; once you understand the equation, you can do any other range calculation. Now, there are several types of DP pressure installations to level measurement; I’ll give you a step by step based on your problem.
Level at 0%
- HP – LP
- (Height H side x Capillary density) – (Height L side x Capillary)
- (1000 x 1.02) – (6000 x 1.02)
- 1020 – 6120
- DP0% = – 5100 mmWC
Level at 100%
- HP – LP
- (Height H process side x Process density) + (Height H side x Capillary density) – (Height L side x Capillary)
- [(5000 x 0.89) + (1000 x 1.02)] – (6000 x 1.02)
- [4450 + 1020] – 6120
- 5470 – 6120
- DP100% = -650 mmWC
Instrumentation training courses:
Other resources that might interest you
Pressure transmitter basics
What are the different types of pressure sensors available in the market?
How to implement a differential pressure flow transmitter to steam flow measurement
I want to learn more about steam flow measurement! Can I implement a standard differential pressure transmitter to the flow measurement?
Pressure transmitter data
I bought a pressure transmitter S/N K219C601052 from Endress+Hauser, but I don’t know if the transmitter is providing the data I requested. Could you check for me?
Lower and upper range values of differential pressure transmitter
On my differential pressure transmitter, I have a range from 0 to 500 psi. We use an orifice plate for creating differential pressure. Maximum DP in our gas flow is about 200 psi but it’s not fixed. Can you tell me how to determine the lower and upper range values?