Multipoint temperature measurement
We’re working on a project to measure 36 temperature points, but we only have 5 HART inputs in our PLC. We’d like multipoint measurement if we can get it. Do you have any suggestions?.
Expert’s answer: Multipoint temperature measurement
OK, so you need help getting multipoint temperature measurement. More specifically, you need it for a project to measure 36 temperature points, but with only 5 HART inputs in your PLC.
Mmm, complex. I like it. Okay, all HART devices work in multidrop installations, and you can have up to 15 devices on the same network. My math says you’d need three networks (15+15+6) to cover all your temperature points, right?
But wait! The Endress+Hauser TMT82 has an option to support two sensors in one transmitter! With the TMT82, you only need two networks. That trims your device count to 18, cutting your costs in half using only 2 HART inputs.
You could also use the TMT82 with a wireless solution. This combination can save you up to 40 percent and provide more information faster than traditional installations. Try it and see!
Where can you get other multipoint temperature measurement solutions?
Want more solutions? Here, we’ve put together some links where you can find more about multipoint temperature measurement.
Other resources that might interest you
Rosemount 3144P temperature transmitter
How do you calibrate or adjust a Rosemount 3144P transmitter?
Temperature transmitter calculations
The output of a temperature transmitter is 13.6. In this case, what are the ideal minimum and maximum temperatures?
Wireless temperature measurement and logging
An application requires a temperature measurement and logging on up to 24 products for 12 hours. So, can the application be measured by a wireless solution?
Temperature measurement between two parts
Are there devices, sensor matrix, and/or material that works between two parts?