I have a 10-meter tank open to atmosphere, with a product density of 0.859 ρ. Which type of pressure transmitter should I use for level measurement? And how do I calculate the level range?
Expert’s answer: Pressure transmitter level calculation
Pressure transmitter level calculation, eh? For this application, use a differential pressure transmitter. Install the transmitter at the tank bottom with the high-pressure side connected to the tank and the low-pressure side open to the atmosphere. Whenever you have a tank open to the atmosphere that needs level measurement based on pressure, use this installation.
Now, you need to find the range. Regardless of the brand, you’ll use the same equation. You need to know the height and the product density to make the calculation.
- height = 10 meters
- density = 0.859
Conversion (mmWC = millimeters per water column)
DP 0% = height x density = 0 mm x 0 density = 0 mmWC
DP 100% = height x density = 10000 x 0.859 = 8590 mmWC
The range of your differential pressure transmitter will be from 0 to 8590 mmWC. You can convert to a different unit if you prefer.
Want more information? If so, here are more pressure transmitters:
Other resources that might interest you
Level calculation for pressure transmitter with capillary
I have a level transmitter with capillary, and I need to do the level calculation. The transmitter is one meter below the takeoff point, and the tank’s takeoff point is five meters. The product’s specific gravity is 0.89, and the capillary is filled with glycol at a specific gravity of 1.02. So how can I calculate the level range?
How to connect a pressure transmitter and HART communicator
I have a question about HART communicators and devices. Can you help? If so, how do I connect a pressure transmitter with a HART communicator?
DP transmitter level calculation
What information do I need to select the pressure cell for a differential pressure transmitter to do level measurement?
Level transmitter calibration!
I’d like to know more about calibration of level transmitters. Do we really need to calibrate these devices?