PROFIBUS DP/PA remote configuration
I have a PROFIBUS network, and I’d like remote access for the field device configuration. We have a Siemens PLC, Pepperl+Fuchs couplers, and other different manufacturers in the network. Can I bypass my PLC with remote access?
Expert’s answer: Is PROFIBUS DP/PA remote configuration possible?
So, a question about PROFIBUS DP/PA remote configuration. Interesting!
The answer is: Of course you can. Let me explain. In PROFIBUS, we can have two masters; the class 1 master communicates actively with configured slaves (devices) and passively with a class 2 master. The class 2 master works as a supervisor, exchanging data with the class 1 and its slaves.
You have a class 1 master, and you can apply a class 2 if you like. You can also buy field gates to provide a remote access to a class 2 master. Depending on your needs, you can choose a gate with network diagnostics and remote access or remote access and field diagnostics.
So the entire solution will combine a field gate with a plant asset management system for remote access. If you don’t have a PAM system you can get diagnostics from the web browser, but not the remote configuration.
Where can you get more information about your PROFIBUS network?
Want more information? Check out the following links to learn more about PROFIBUS networks:
Other resources that might interest you
PROFIBUS PA and PROFIBUS DP
Why should you have PROFIBUS PA? Can you implement every device you have in the PROFIBUS DP network?
Terminator on PROFIBUS network!
Why do you need a terminator in your PROFIBUS network? What would happen if you left it out?
PROFIBUS Class 1 and Class 2 masters!
What’s the difference between a Class 1 and a Class 2 master on a PROFIBUS network?
PROFIBUS cost of investment
How do I calculate the cost per device for a PROFIBUS network?