Rosemount 1151 pressure transmitter manual
We have an old Rosemount 1151 available in our inventory but I can't find the manual for it. Could you please provide it?.
Expert answer: Rosemount 1151 pressure transmitter manual
Before we hook you up with the Rosemount 1151 pressure transmitter manual, let’s talk about the good old Rosemount 1151 and its replacements. You can find the link at the bottom if you need it right now. If not, then pull up a chair and have a read.
The 1151, a differential pressure (DP) transmitter from Emerson Automation Solutions, spent 40 years in the industry before Emerson discontinued it in 2011. Like any other DP transmitter, it measured flow, level, and of course, pressure. It came in two models, one analog, the bare-bones basic model, and the other the smart device.
The housing of the smart device had two buttons, zero and span, to set the upper and lower range values (URV and LRV) in the field. It also had two switches. The write-protect switch prevented changes to the configuration data, and the failure mode switch allowed you to set the failure mode to high or low. Besides those features, the smart device could also use HART over analog to give you digital communication.
Emerson offers two replacement options for the 1151. If you go to Emerson’s website, it’ll suggest the 3051. However, Emerson also has a simpler and cheaper version, the 2051. The 3051 has more wetted part options and a bigger rangedown (150 to 1 against the 2051’s 100 to 1). It also has the option of Power Advisory Diagnostics in addition to the basic diagnostics of the 2051. The two devices have slightly different designs as well.
But let’s get back to your question, the manual. You can find the Rosemount 1151 pressure transmitter manual here. Hope you enjoyed the trip down memory lane!