I have a pressure device installed for level measurement, and now the operator wants to receive data on the tank volume. Can I do that using the pressure device?
Fabrício AndradeSep 29, 2016
Expert’s answer: Volume measurement from pressure transmitter
Yes, volume measurement from pressure transmitter is possible. But to enable volume measurement, you need to create a linearization table with the pressure in the X column and volume in the Y column. You also need the pressure per volume data and more time for the transmitter setup.
This information can enable the pressure transmitter to begin volume or mass measurement. So if you want a device that will do all that for you, there are many level radars on the market with that functionality built in.
Want more information? In that case, here are a few companies that offer them:
Radar or pressure transmitter? Nowadays, I see a lot of recommendations to use radar for level measurement. So would it benefit me to switch from a pressure transmitter to a radar level meter?
Pressure transmitter level calculation I have a 10-meter tank open to atmosphere, with a product density of 0.859 ρ. So, which type of pressure transmitter should I use for level measurement? And how do I calculate the level range?
Wenn Sie eine ähnliche Geschichte haben, die Sie gerne teilen möchten, schreiben Sie uns und wir melden uns zurück